  <Contents>
  
	  <Content id="" Class="SimpleText" DefaultType="PageHeading">
		  <P1><![CDATA[Non-DSC Panel: Bell Follower Mode]]></P1>
		  <P2 _x="" _y="" RelativeGapY="" FadeEffect="true" FadeSpeed="25"/>
		
	  </Content>

	<Content id="" Class="Audio" DefaultType="Audio">
		<P1><![CDATA[]]></P1>
		<P2 AudioPath="swfs/module3/tl_mod03_p04.swf"/>
	</Content>
	
		
	<Content id="" Class="Bullets" DefaultType="Level1" Type="Special" SpId="A1">
		 <P1><![CDATA[Connect a 12VDC power supply to &#x2B;12V and GND]]></P1>
		 <P2 _x="" _y="120" RelativeGapY="" _width="" RemoveCompareId="A1"/>
	</Content>

	<Content id="" Class="Bullets" DefaultType="Level1" Type="Special" SpId="A2">
		 <P1><![CDATA[Connect a relay to the bell output of the control panel. The relay must match the power output of the control panel. Connect the normally-closed output of the relay to IN1 and GND]]></P1>
		 <P2 _x="" _y="" RelativeGapY="" _width="" RemoveCompareId="A2"/>
	</Content>

	<Content id="" Class="Bullets" DefaultType="Level1" Type="Special" SpId="A3">
		 <P1><![CDATA[Connect the RJ45 network cable to the RJ45 network jack on the TL250]]></P1>
		 <P2 _x="" _y="" RelativeGapY="" _width="" RemoveCompareId="A3"/>
	</Content>

	  	
	<Content id="" Class="Transcript" DefaultType="Transcript">
		<P1><![CDATA[The TL250 can also be connected to a non-DSC panel using the Bell Follower Mode.<br>Step 1: Connect an external 12 volt DC power supply to the plus 12 volt terminal of the TL250. Then connect the ground terminal of the power supply to the ground terminal of the TL250.<br>Step 2: Connect a relay to the bell output of the control panel. The relay must match the power output of the control panel. Connect the normally-closed output of the relay to input one and ground. Input 1 must be used for this application.  At default, Input 1 is configured to be violated when a short to ground is detected.  When using the Bell Follower Mode, the TL250 monitors the status of input 1.<br>If a steady short to ground is detected, the TL250 transmits a burglary alarm.  If a pulsing short to ground is detected (including temporal patterns) the TL250 transmits a fire alarm. A restoral is transmitted when the short between Input 1 and ground is removed.<br>Step 3: Connect the RJ45 network cable to the RJ45 network jack on the TL250. Before connecting the RJ45 network cable to the RJ45 network jack on the TL250, ensure the TL250 is programmed correctly.]]></P1>
	</Content>
  </Contents>


